* Estimated shipping rate for US 48 states. Final rate calculated at checkout.
|Home » |
ICM280 Goodman Furnace Control Circuit Board
ICM280 Goodman Furnace Control Circuit Board FEATURES Includes flash code diagnostics. Twinning. Includes mounting hole template. Fused to protect low voltage system transformers. Adjustable blower relay. 90+ furnace option. SPECIFICATIONS Operating Temperature . .-40 to 176F Humidity Range . . 95% RH (non-condensing) Mounting . . . Plastic standoffs Electrical Ratings @ 77F (25C) Input Voltage . . . 20-30 VAC RMS 50/60 Hz Maximum Input Current @ 30 VAC 0.35 amp Relay Load Ratings Valve Relay 1.5 amp @ 30 VAC 50/60 Hz 0.6 pf Ignitor Relay . . . 5.0 amp @ 120 VAC 50/60 Hz Inducer Relay . . . 4.0 FLA-8.0 LRA @ 120 VAC Circulator Relay . . .14.5 FLA-25.0 LRA @ 120 VAC Flame Current Requirements Minimum current to insure flame detection . . . 75 uA DC Maximum current for non-detection . . . . . . . . 0.10 uA DC Maximum allowable leakage resistance . . . . . 100 M ohms
|Average Customer Rating:
|| based on 6 reviews|
Average Customer Review:
( 6 customer reviews )
Write an online review and share your thoughts with other customers.
Most Helpful Customer Reviews
2 of 2 found the following review helpful:
Goodman Furnace Control BoardDec 11, 2010
By K. Weerts
This board arrived quickly and allowed me to put my furnace back into operation right away. It was the current replacement model for the failed board. Good price too!
Goodman B18099-06 To ICM280 replacement furnace controllerJan 06, 2013
By Daniel Pomales
I have a old GMP075-03 furnace with a B18099-06 controller board. I could not afford to pay a HVAC company $500.00 or more dollars to fix my furnace. The furnace was intermittently turning off. It took multiple attempts for the furnace to ignite. I replaced the flame sensor to no avail. I replaced the pressure switch to no avail. I tested and reset the flame rollout switches to no avail. The igniter finally failed and had to be replaced. I paid $38.00 for the pressure switch, $18.00 for the flame sensor, $60.00 for the igniter and $90.00 for the ICM280 furnace controller. I ended up spending $206.00 total to fix the furnace. The ICM280 furnace controller is a excellent replacement controller for my old Goodman Janitrol GMP075-03 furnace. It works great! Follow the instructions and you cannot go wrong. I labeled all of the wires on the old controller before I pulled them off. I cut the white jumper between pins 1 and 4 on the 9 pin connector. I wired up the 24 volt transformer connection as instructed. I connected the R, G and W thermostat wires as instructed. I turned on the gas and electricity and everything started working like new! Problem resolved!
furnaceNov 05, 2012
The product worked well, it was fast delivery, everyhing was in order and it did a great job. I was very pleased with the condition it came in and how easy it was to hook back up.
great item!Nov 03, 2012
By Dave Devitt
Item was exactly as described. received quickly & required no modification what so ever. had it installed in less than 30 minutes & furnace began working perfectly! Thanks!
1 of 2 found the following review helpful:
Speedy delivery!Oct 22, 2011
I ordered this product on Wed. evening October 19, 2011. It arrived on the morning of October 22, 2011. It was well-packaged and in excellent shape. I was concerned it was the wrong part, but it clearly states on the box that it will work in my Goodman furnace(part no. B1809913S). I am a home owner who will be replacing this myself. Wish me luck.
See all 6 customer reviews on Amazon.com